Crown Boiler Recalls Home Heating Boilers Due to Carbon Monoxide Hazard
Washington, DC, December 2013 — Crown Boiler has recalled home heating boilers due to carbone monoxide hazard. The air pressure switch can fail to shut down the burners in the event that there is a blockage in the vent system allowing the boiler to emit excessive amounts of carbon monoxide, posing a CO poisoning hazard to the consumer.
Name of product: Gas-fired hot water boilers
Hazard: The air pressure switch can fail to shut down the burners in the event that there is a blockage in the vent system allowing the boiler to emit excessive amounts of carbon monoxide, posing a CO poisoning hazard to the consumer.
Consumer Contact: Crown Boiler Company toll-free at (855) 688-0776 from 8 a.m. to 5 p.m. ET, e-mail firstname.lastname@example.org or online at www.crownboiler.com and click on CPSC Product Recall Announcement for more information.
Units: About 2,200
Description: This recall involves Crown Boiler CWD series cast iron hot water boilers that use natural gas or liquid petroleum to heat water in home baseboard, floor or radiator heating systems. The boilers are red and gray, about 37 inches tall, about 23 inches deep and range from about 16 to 42 inches wide. The Crown Boiler logo is on the front of the boiler. Recalled boilers have model numbers that begin with CWD and were manufactured between May 1, 2005 and July 1, 2013. The model number and the manufacturing date are located on a white rating label located on the upper right side of the boiler. The manufacturing date appears under “Series” in the MM/DD/YYYY or M/D/YYYY format or as a two-letter code. Recalled models have dates between 5/1/2005 and 7/1/2013 or one of the following two-letter codes:
EB, FB, GB, HB, IB, JB, KB, LB
AC, BC, CC, DC, EC, FC, GC, HC, IC, JC, KC, LC
AD, BD, CD, DD, ED, FD, GD, HD, ID, JD, KD, LD
AE, BE, CE, DE, EE, FE, GE, HE, IE, JE, KE, LE
AF, BF, CF, DF, EF, FF, GF, HF, IF, JF, KF, LF
AG, BG, CG, DG, EG, FG, GG, HG, IG, JG, KG, LG
AH, BH, CH, DH, EH, FH, GH, HH, IH, JH, KH, LH
AI, BI, CI, DI, EI, FI, GI, HI, II, JI, KI, LI
AJ, BJ, CJ, DJ, EJ, FJ.
Incidents/Injuries: None reported.
Remedy: Consumers with recalled boilers should immediately contact the installer or distributor from whom they purchased the boiler or Crown Boiler to schedule a free in-home repair. Consumers who continue using the boilers while awaiting repair, should have a working carbon monoxide alarm installed outside of sleeping areas in the home.
Sold at Plumbing and heating wholesale distributors nationwide from May 2005 through July 2013 for between $4,000 and $6,700.
Manufacturer: Crown Boiler Company, of Philadelphia
Manufactured in: United States
The U.S. Consumer Product Safety Commission is charged with protecting the public from unreasonable risks of injury or death associated with the use of thousands of types of consumer products under the agency’s jurisdiction. Deaths, injuries, and property damage from consumer product incidents cost the nation more than $1 trillion annually. CPSC is committed to protecting consumers and families from products that pose a fire, electrical, chemical or mechanical hazard. CPSC’s work to help ensure the safety of consumer products – such as toys, cribs, power tools, cigarette lighters and household chemicals -– contributed to a decline in the rate of deaths and injuries associated with consumer products over the past 40 years.
Federal law bars any person from selling products subject to a publicly-announced voluntary recall by a manufacturer or a mandatory recall ordered by the Commission.
To report a dangerous product or a product-related injury go online to www.SaferProducts.gov or call CPSC’s Hotline at (800) 638-2772 or teletypewriter at (301) 595-7054 for the hearing impaired. Consumers can obtain news release and recall information at www.cpsc.gov, on Twitter @OnSafety or by subscribing to CPSC’s free e-mail newsletters.